Full-Text Search：
《High Voltage Engineering》 2006-12

## Study on Radio Interference of AC UHV Double Circuit Transmission Lines on the Same Tower

WAN Baoquan, WU Xiong, LU Yao, ZHANG Xiaowu (Wuhan High Voltage Research Institute of SGCC, Wuhan 430074, China)
AC UHV power transmission has become the strategy and program of building strong electric power grids in our country for it can transmit high voltage and long way and realize electric resource optimizing collocation in a wide range. Compared with single-line, same tower double-line has the advantage of reducing the line corridor and saving the land resource, optimizes the arrange way of conductor at the same time ,and reduces electric and magnetic field on the ground, so it could become a important way of developing AC UHV power transmission in our country. The problem of electro-magnetic environment is the key technique problem in building UHV power transmission. Radio interference as the characteristic of conductor corona will directly influence the choice and arrange way of the line conductor and the settlement of the height the conductor to the earth and the tower type. This study carried out the calculation and analysis on the radio interference of AC same tower double UHV power transmission and proposed the line parameter satisfied with the request of radio interference. We can draw the conclusion as follows: 1)1000kV double circuit on one tower, the two kind of tower, the cross-section is larger than 8×LGJ-630, mentioned above. The value of radio interference below 55dB(μV/m). To satisfy the limit of 58dBμV/m, the height of conductor should be increase in a large range when it is arranged in inverse array of phase. 2) The same array of phase can reduce the value of radio interference, but will increase the electric intensity on the ground. As a result, when we choose the array of the conductor, we should consider the two factors. 3) The tower 1 is recommended as a result of considering of reducing the radio interference.
【Key Words】： AC UHV same tower double circuit power transmission line radio interference
【CateGory Index】： TM723
CAJViewer7.0 supports all the CNKI file formats; AdobeReader only supports the PDF format.
 【References】
 Chinese Journal Full-text Database 7 Hits
 1 YANG Guang,Lü Ying-hua (School of Telecommunication and Network Technology,Beijing University of Posts and Telecommunications, Haidian District,Beijing 100876,China);Radio Interference Characteristic of UHVAC Transmission Lines[J];Power System Technology;2008-02 2 ZHAO Yu-ming,MA Min-hua,GUAN Zhi-cheng,HUI Jian-feng,WANG Li-ming,LI Qiu-wei(Graduate School of Shenzhen,Tsinghua University,Shenzhen 518055,China);Influence of Contaminations of the Conductor on HVDC Transmission Line Corona Characteristics[J];High Voltage Engineering;2007-12 3 ZHANG Guang-zhou, ZHANG Ye-mao, WAN Bao-quan, WU Xiong(State Grid Electric Power Research Institute, Wuhan 430074, China);Optimization of Conductor Configuration for UHV Double-circuits Transmission Lines[J];High Voltage Engineering;2008-09 4 LIANG Ming, WANG Yong-gang, ZHOU Gang(Southwest Electric Power Design Institute, Chengdu 610021, China);Choice of Bundle Conductor for ±800 kV DC Overhead Power Transmission Lines Based on Corona Performance[J];High Voltage Engineering;2008-09 5 TIAN Qing(Southeast Shanxi Ultra High Voltage Administrative Bureau, State Grid Operation Company, Limited, Changzhi 047100, China);Choice of Neutral Inductance and Insulation Level of Shunt Reactor Neutral Point in UHV AC Pilot Project[J];High Voltage Engineering;2009-03 6 WAN Bao-quan1,WU Xiong1,ZHANG Ye-mao1, CAO Sheng-shun2,ZHU Yue2,LIU Da-shi 2(1. State Grid Electric Power Research Institute, Wuhan 430074, China; 2. Northwest China Grid Company, Limited, Xi’an 710048, China);Electromagnetic Environment of 750 kV Single-circuit Compact Transmission Lines[J];High Voltage Engineering;2009-03 7 ZHANG Xiao-wu, GAN Zhe-yuan (State Grid Electric Power Research Institute, Wuhan 430074, China);Reradiate Computation Model of Transmission Line to the Shortwave[J];High Voltage Engineering;2009-04
 【Citations】
 Chinese Journal Full-text Database 1 Hits
 1 ;The Present Situation of 1150kV Transmission of USSR[J];High Voltage Engineering;1991-04
 【Co-citations】
 Chinese Journal Full-text Database 10 Hits
 1 WANG Qun, LI Yong-qin, CHEN Jing, ZHOU Mei-ling (College of Material Science and Engineering, Beijing University of Technology, Beijing 100022, China);Analysis and Assessment of Electromagnetic Field Under 110 kV High Voltage Transmission Lines[J];Journal of Beijing Polytechnic University;2005-03 2 Liu Xiaojun , Yuan Qi, Mo Guihua (Electric Engineering Academy of Wuhan University , Wuhan High Voltage Research Institute );The Study of Power-frequency Electric Field under the AC 500kV Transmission lines of Sanxia Power Station Crossing over the Permanent Ship Lock[J];Marine Electric & Electric Technology;2002-01 3 Zhu Jinglin, Fu Zhengcai, Liu Wenxun(Electrical Engineering Department of Shanghai JiaoTong University Shanghai 200030);The Application of Charge Simulation Method in the Electric Field Calculation for Substation[J];Electric Engineering;2006-12 4 ZHANG Yang,GUO Ming-fan;Impact and prevention measures for electromagnetic field of extra high voltage transmission lines[J];Electric Power Environmental Protection;2007-04 5 ZHAO Su-li,SHI Yu-zhu;Discussion on necessity of substation electromagnetic environment protection district[J];Electric Power Environmental Protection;2008-03 6 WANG Feng-ying,WANG Wen-bing;The electromagnetic effect of ultrahigh voltage transmission and transfer power engineering and its prevention methods[J];Electric Power Environmental Protection;2008-03 7 LI Xue-liang,ZHU Geng-fu,LI Xiao-qin;Analysis on environmental requirements and development trend of power transformation construction projects[J];Electric Power Environmental Protection;2008-06 8 PU Wen-qing,WANG Sheng,SONG Yan-yan,et al;The perception & practice on transmission electricity Environmental Impact Assessment[J];Electric Power Environmental Protection;2009-02 9 REN Wen-chun;High-voltage power transformission project electromagnetic field environmental impact and its countermeasure[J];Electric Power Environmental Protection;2009-02 10 Mao Wenqi 1,Liu Haiyan 2,Xu Hua 2,Huang Wenwu 2 (1.Huan Provincial Electric Power Test Institate,Changsha,410007; 2.Wuhan University,Wuhan,430072);Discussion about Impact of EHV Transmission on Environment[J];Electric Power Construction;2004-08
 【Co-references】
 Chinese Journal Full-text Database 10 Hits
 1 CHEN Shui ming WANG Lei HE Jin liang (Department of Electrical Engineering, Tsinghua University, Beijing 100084, China);Radio interference analysis from multi-circuits AC high voltage overhead power transmission lines[J];Chinese Journal of Radio Science;2002-06 2 ;Study of electromagnetic noise influence from corona on high voltage transmission lines[J];Electric Power Environmental Protection;2004-03 3 Sui Xiaojie,Song Shouxin(Beijing Jiaotong University,Beijing City,100044);Analysis on Corona Discharge of HV Transmission Lines[J];Electric Power Construction;2006-03 4 Li Bin , Li Yongli , He Jiali , Zheng Yuping , Sheng Kun , Guo Zheng ( Tianjin University, Tianjin 300072, China) ( Nari-Relays Electric Co Ltd, Nanjing 210003, China);RESEARCH ON PROTECTIVE RELAYING AND SINGLE-PHASE RECLOSURE OF 750 kV TRANSMISSION LINE[J];Automation of Electric Power Systems;2004-13 5 NIU Lin,DU Zhi-gang,ZHAO Jian-guo (School of Electrical Engineering,Shandong University, Ji'nan 250061,China);Calculation and characteristic analysis of surface voltage gradient for UHV transmission conductor bundle[J];Electric Power Automation Equipment;2007-10 6 WU Jing-ru1,XU Yong-xi2 (1.China Development Bank,Xicheng District,Beijing 100037,China;2.China Huaneng International Trade-Economic Corporation,Haidian District,Beijing 100036,China);DEVELOPMENT PROSPECT OF UHV AC POWER TRANSMISSION IN CHINA[J];Power System Technology;2005-03 7 SHAO Fang-yin (China Electric Power Research Institute,Haidian District,Beijng 100085,China);PHASE CONDUCTOR CONFIGURATION AND POWER FREQUENCY ELECTROMAGNETIC ENVIRONMENT OF UHV TRANSMISSION LINES IN CHINA[J];Power System Technology;2005-08 8 WU Gui-fang (China Electric Power Research Institute,Haidian District,Beijing100085,China);ELECTROMAGNETIC ENVIRONMENT PROBLEM BROUGHT ABOUT BY ±500kV DC TRANSMISSION PROJECT IN CHINA[J];Power System Technology;2005-11 9 ZHOU Hao,YU Yu-hong (College of Electrical Engineering,Zhejiang University,Hangzhou 310027,Zhejiang Province,China);DISCUSSION ON SEVERAL IMPORTANT PROBLEMS OF DEVELOPING UHV AC TRANSMISSON IN CHINA[J];Power System Technology;2005-12 10 SHU Yin-biao, LIU Ze-hong, YUAN Jim, CHEN Ge-song, GAO Li-ying (UHV Office of State Grid Corporation of China, Xicheng District, Beijing 100031, China);A Survey on Demonstration of UHV Power Transmission by State Grid Corporation of China in the Year of 2005[J];Power System Technology;2006-05
 【Secondary References】
 Chinese Journal Full-text Database 9 Hits
 1 LI Xian-xin1,GUO Yong-hua2,TANG Ming-gui2 (1.State Power Economic Research Institute,Xuanwu District,Beijing 100761,China; 2.Henan Electric Power Survey & Design Institute,Zhengzhou 450007,Henan Province,China);Planning Research on Single-Pole-Combined Strain Tower for 1000kV AC Double-Circuit Transmission Line[J];Power System Technology;2009-07 2 ZHAO Yu-ming1,MA Min-hua2,CHU Jin-wei1,GUAN Zhi-cheng1,WANG Li-ming1(1.Graduate School at Shenzhen,Tsinghua University,Shenzhen 518055,China;2.Guangdong Electric Power Design Institute,Guangzhou 510600,China);Measurement Methods for DC Conductor Corona Onset Voltage in the Corona Cage[J];High Voltage Engineering;2008-08 3 BIAN Xing-ming1,2,ZHANG Fu-zeng2,WANG Li-ming1,2,GUAN Zhi-cheng1,2,WANG Lai3,CHEN Yong4,BO Xue-wei5,REN Gui-qing5(1. Department of Electrical Engineering,Tsinghua University,Beijing 100084,China; 2. Graduate School at Shenzhen,Tsinghua University,Shenzhen 518055,China; 3. China Electric Power Research Institute,Beijing 100192,China; 4. State Grid Electric Power Research Institute,Wuhan 430074,China; 5. Dalian Insulator Corporation,Dalian 116600,China);Design of Grading Rings for 1000kV AC Composite Insulator[J];High Voltage Engineering;2009-05 4 TIAN Qing(Southeast Shanxi Ultra High Voltage Administrative Bureau,State Grid Operation Company,Limited,Changzhi 046603,China);Configuration of Transformer Protection in UHV AC Pilot Project[J];High Voltage Engineering;2009-07 5 TAN Wen1,ZHANG Xiao-wu2(1.College of Electrical and Electronics Engineering,Huazhong University of Science and Technology,Wuhan 430074,China;2.State Grid Electric Power Research Institute,Wuhan 430074,China);Research Review on Audible Noise Control of Transmission Line[J];High Voltage Apparatus;2009-03 6 GUAN Zhi-cheng1,CHU Jin-wei1,ZHAO Yu-ming2,BIAN Xing-ming1,WANG Li-ming1(1.Graduate School at Shenzhen,Tsinghua University,Shenzhen 518055,China;2.Technology Research Center,China Southern Power Grid,Guangzhou 510620,China);Simulation for the Influence of Contamination Particulates on Surface Electric Field of HVDC Transmission Conductor[J];High Voltage Engineering;2009-09 7 CHEN Zhong1,2,CAI Ze-xiang2(1.Maintenance & Test Center of EHV Power Transmission Company of China Southern Power Grid,Guangzhou 510663,China;2.South China University of Technology,Guangzhou 510160,China);On-site DC Voltage Withstand Test of ±800 kV DC Equipment[J];High Voltage Engineering;2009-10 8 LIU Bing1,RUAN Jiang-jun1,HAN Hai-hong2,YU Shi-feng1,WU Tian1(1.School of Electrical Engineering,Wuhan University,Wuhan 430072,China;2.Jinzhong Power Supply Branch Company,Shanxi Electric Power CO.,Ltd.,Jinzhong 030600,China);Analysis of Electromagnetic Environment of VSC-HVDC[J];High Voltage Engineering;2009-11 9 LIU Jie,ZHAO Zhi-bin,CUI Xiang(School of Electrical and Electronic Engineering,North China Electric Power University,Baoding 071003,Hebei Province,China);Radio Interference Calculation of Four Circuits Belonging to Different Voltage Classes on Same Tower by Hybrid Method[J];Power System Technology;2009-20
Similar Journals
 > Jiangxi Electric Power > Hubei Electric Power > Journal of Electric Power Science and Technology > Journal of Lanzhou Jiaotong University > Electric Machines & Control Application > Relay > High Voltage Engineering > Electric Power Construction > Power System Technology > Packaging Engineering