Cause Analysis and Prevention Measures of Voltage Transformer Explosion
YUE Gang;Lijiang Power Supply Bureau,Yunnan Power Grid Co.,Ltd.;
Aiming at the 35 kV voltage transformer explosion fault in the operation,the reason was analyzed combined with on-site inspection and ferromagnetic resonance simulation technology.The rectification measures were propsed.
【CateGory Index】： TM451